This document covers the monitoring of air cleanliness by particles in terms of concentration of airborne nanoscale particles.
For monitoring purposes, only populations of particles with a lower size limit of 0.1 microns (100 nm) or less ? "nanoscale" ? are considered.
The monitoring given in this document is for use mainly in "operational" states.
NOTE 1 For the purposes of this document, reference is made to "nanoscale particles", which means all nano-objects having one (nanoplate), two (nanofibre) or three (nanoparticle) dimensions in the nanoscale.
NOTE 2 As a consequence, the specifications for monitoring air cleanliness by nanoscale particle concentration of the cleanroom in operational state also considers process specifics, e.g., used equipment, personnel behaviour, etc.
NOTE 3 Health and safety considerations are excluded from this document.
Status: PublishedPublication date: 2018-08
Edition: 1Number of pages: 11
Technical Committee: ISO/TC 209 Cleanrooms and associated controlled environments
Buy this standard
|std 1 58||PDF + ePub|
|std 2 58||Paper|